Wire the siren driver to the control and to the speaker s. General Information Users of the system may periodically receive messages on their display screens from their monitoring agency or installer. This allows viewing only of that partition. Run wires from the control panel to each device on the polling loop see Figure 3-13. As part of its fail-safe software, the control limits all audio alarm verification sessions to 15 minutes. Use 93 Menu Mode, Zone Programming to program the response types.
Refer to the Programming Guide for details. If enabled, selects Sescoa, which uses only numeric reporting 0-9. Use 93 Menu Mode, Zone Programming to program the response types. The user should then press the button again within 4 seconds to force-bypass those zones and arm the system. If not required, enter nothing and proceed to next field.
To wire 2-wire smoke detectors to zone 1, perform the following steps: Step 1 2 3 Action Select up to 16 2-wire smoke detectors from the list of compatible detectors. It is the only format capable of uniquely reporting all 86 zones, as well as openings and closings for all 75 users. Enter Master or Manager code and press the Ê8Ê. Restrict Disarming This option allows disarming by users only during the disarm time window and during the arming time window in case user needs to re-enter premises after manually arming the partition. Daily Schedule Each partition can have one daily schedule consisting of one opening window and one closing window per day. It listens for TouchTones on the phone line and reports them to the control panel.
When all partition-specific fields are programmed, the system returns to the global programming fields page 1 fields. Late Closing reports are sent if system is manually armed after the closing window expires. The panel arms at the conclusion of the Auto-Arm Warning period. Temporary Schedule The temporary schedule provides a method for the end user to override the daily and holiday schedules. Backs up to previous screen.
X-10 devices require the use of a 1361X10 transformer in place of the regular 1361 transformer. Enter the 2-digit time window number 01-20 to be programmed. The zone displays on the keypads, reports to the event log, and transmits to the central station if programmed on Partition 1. A Master keypad uses the same panics as Partition 1. They do not send low-battery signals until they are activated. The keyswitch can operate in only one particular partition.
Enter the report code 01-15 for each type of report. Refer to Limitation of Access Schedules Programming later in this section for detailed procedures. However, there are some things you can do to make sure that your system is in reliable working condition. If dual receivers are used: a. Supervised transmitters send a supervisory signal every 70-90 minutes. This schedule takes effect as soon as it is programmed, and remains active for up to one week. In Table 4, enter the total calculated subtotals of all listed outputs from Tables 1 through 3, then add to get the combined current.
Mounting the Control Cabinet To mount the control cabinet, perform the following steps: Step 1 Action Before mounting the circuit board, remove the metal knockouts for the wiring entry that you will be using. Refer Figure 3-22 for wiring connections. During off-premises phone access, it seizes the line from the premises phones and any answering machines. Experienced installers can simply follow this column when programming the data fields. We recommend that spacing between fire cross-zones be no farther than 30 ft. If a relay is programmed to activate on a fault of one of the zones, the relay activates without the other zone being faulted. Start Data Field programming by entering the installer code + 8 + 0 + 0.
This system offers you three forms of protection: burglary, fire and emergency. When the last day of the week has been programmed, the windows for holidays may be entered. Entry Delay 2 is used for a secondary door requiring a longer delay than those assigned to Entry Delay 1. They must be set for different addresses. These commands are known as a macro and are stored in the system's memory. Exit delay begins whenever the control is armed, regardless of the arming mode selected. At the expiration of this delay, the Auto-Arm Warning will start.
Scheduling Program Mode can be entered only when all partitions are disarmed. This is done by entering a keypad command User Code + 82 , which then prompts the user to enter the desired extension time of 1 or 2. Any zone from 1 to 86 can be used as a 5800 Series wireless zone, with the exception of zone 64 reserved for a wireless keypad. This field has five two-digit entries as follows: Alarm Restore, Trouble, Trouble Restore, Bypass, and Bypass Restore. The transmitter may be carried off-premises. Can control 8 separate areas independently, each functioning as if it had its own separate control. If you are mounting remotely, homerun each module to the control.
User 2 has access to Office 2 and the Common Lobby. As the number is keyed in, the actual time that has been stored for the window is displayed. A subsequent short across Zone 7 clears the alarm memory indication and resets 2-wire smoke and glassbreak detectors if used. Installing the 4204 Relay Modules Each 4204 module provides 4 relays with Form C normally open and normally closed contacts. The back of the cabinet has 4 holes for this purpose.